Evaporative /outdoor air coolers :
Wide range of evaporative air Coolers in our catalogue, below only few.
The evaporator cooler outlet temperature is too low, increase evaporator cooler ash conveying system maintenance volume, seriously affect the converter production, and the temperature is too low smoke. Evaporative cooler temperature control system is not only related to the converter once the dust removal effect is also related to the normal production of the converter smoothly.
Air evaporative cooling air conditioning system design calculation steps:
- To determine the design object: to determine the type of building to determine the suitability of water-air-conditioning system. Currently in hotel rooms, offices, hospitals and other buildings in large-scale use.
- To determine the outdoor air-conditioning design parameters in summer: according to the design of the target area, in the corresponding region of the enthalpy chart to determine the location of the summer outdoor air state point, outdoor air temperature calculated by the summer outdoor, summer air conditioning Outdoor wet-bulb temperature is to determine.
- Determine the summer indoor design state point: According to the function and requirements of the building object, determine the summer indoor air state point, through the summer air conditioning indoor design dry bulb temperature summer air conditioning indoor design relative humidity to determine.
- This paper introduces the design calculation method and the checking calculation method of water – air evaporative cooling air conditioning system. The design process of water – air evaporative cooling air conditioning system is described in detail.The design of water – air evaporative cooling air – conditioning system, the design, check, determination and selection of each parameter are introduced. Look for the future evaporative cooling air conditioning system design standards and technical regulations play an active role in the formulation.